The GE Hydran Ti is a small on-line early warning transmitter. It is permanently mounted on the transformer and will provide personnel with a single reading. The Hydran Ti is a small and easy to setup continuous DGA monitor. It provides the basic information used by IEEE® Standard C and can be used as. GE Hydran Ti | Single Gas Transformer DGA. Basic transformer monitoring device comprised of a fault gas sensor (Ti) and a separate controller (Ci) .
|Published (Last):||28 December 2007|
|PDF File Size:||14.64 Mb|
|ePub File Size:||2.43 Mb|
|Price:||Free* [*Free Regsitration Required]|
This means the product has been inspected, cleaned, and repaired to meet manufacturer specifications and is in excellent condition. This value can be downloaded and alarms can be set at pre-determined levels to alert hydrqn and enable monitoring of the developing fault condition. Back to home page. This location presents the HTi with the best combination of oil flow, temperature and ease of access.
MD Single Gas-Hydran 201Ti
Use a bucket to collect the oil. Ideal for Transmission transformers. For additional information, see the Global Shipping Program terms and conditions – opens in a new window or tab This amount includes applicable customs duties, taxes, brokerage and other fees. Resume making your offerif the page does not update immediately.
Hydran Ti – GE Distribution Products – Ürünlerimiz | EKOS GROUP
The value on the Test Certificate and Data Sheet 4. Report item 21ti opens in a new window or tab. One Hydran TW tube wrench per site is recommended. Image not available Photos not available for this variation. Drain valve bottom of tank: In terms of performance excellent convective oil flowthis location is a very good alternative location to install the HTi.
HYDRAN Ti communication driver
However, the information contained in this manual is subject to change without notice, and does not 20ti a commitment on the part of General Electric Canada. Any included or attached hardware schematics and technical descriptions, or software listings that disclose source code, are for information purposes only. Subject to credit approval.
Connect the other end of the cable to the hydra source. Galvanized fittings pipes, reducing bushings, rings, etc. The item may be missing the original packaging, or in the original packaging but not sealed. Select a valid country. Add to watch list Remove from watch list.
Do not install the HTi on the inlet side of the radiator pump see Figure on page The condition of any tests shall be mutually agreed upon and General Electric Canada shall be notified of and may be represented at all tests that may be made. The item may be a factory second or a new, unused item with defects.
Contact the seller – opens in a new window or tab and request a shipping method to your location. Follow the company regulations meticulously. Pipe wrench to tighten the brass adaptor onto the valve? See terms – opens in a new window or tab.
Real-time single composite fault-gas measurement system. You may not disclose, reproduce, publish, license, post, transmit or distribute this manual, in whole or in part, without the prior written permission of General Electric Canada or except as permitted by written license agreement with General Electric Canada.
Screw the adaptor onto the valve and tighten it using a pipe wrench. This indicates the sensor is being heated. Figure – Do Not Touch the Membrane. Be the first to write a review. Subject to credit approval. Appendix A Electrical Connections.
The HTi must always be grounded, even if the transformer tank is grounded at a single point and monitored for tank-to-ground currents. Back to home page. See other items More Modbus or Hydran protocols available. Separate the adaptor and the heating plate.
Hydran 201Ti Transformer Monitoring System
Report item – opens in a new window or tab. Drill, bits and fasteners for mounting the Hydran Ci Controller? Run the alarms cable through the second conduit up to the HTi. Proceed carefully to avoid introducing air into the transformer.